Digital Display Floor Heating Temperature ControllerDelivery term:The date of payment from buyers deliver within days
- Total supply:
- Delivery term:
The date of payment from buyers deliver within days
- Validity to:
- Last update:
- Browse the number:
XMTA-1001 digital temperature controller
XMTA-1001 series temperature controller applies special technique to resist interference and adopts digital display of measure temperature and method of time proportion control. It has high precision、good reliability、strong cushioning、easy installation and so on. This controller is widely used as temperature measurement and control automatically in light and heavy industry ,such as ,metallurgy、chemical、electronic、machinery、textile、plastic、refrigeration、medical treatment、electric oven and so on..
1、Input type: K
3、Accuracy: ≤ 1.0%FS ±1B
4、Contact capacity: 220VAC, 7A(resistance load)
5、Power supply: AC85～242V , 50Hz
6、Power consumption : ＜ 3W
7、Overall size and installation hole : 96×96×85mm ; 92×92mm
8、Working environment: temperature: 0～50℃; relative humidity: ＜85% RH, without corrode gas .
C. Method to use:
Connect the power and the sensor according to the connection Scheme，then it displays the actual measure temperature.
The terminals of ‘1’, ‘2’ are input of thermocouple signal, the terminals of ‘12’, ‘13’, ‘14’ are relay control output. “14” is higher, “13” is general, “12” is lower. The terminal of ‘15’, ‘16’ are power supply (AC85～242V).
When the temperature-setting is higher than the indicated value, the general and lower voltages are connected, while general and higher voltages are disconnected with green indicator bulb lighting up; the setting is lower than the actual indication, the general-lower voltages are disconnected and the general-higher voltages are connected with the red indicator bulb lighting up.
D.The maintenance and attention of controller.
1.The controller should be installed in the condition without corrode gas.
2.Thermocouple should be put in the place where it can measure real temperature inside the furnace and has good insulation with heating element of furnace.
3.Before powering on the controller, please check it carefully to see if all connection is correct and if thermocouple can match with input type of controller.
4.When heating initially, although the power of heating element inside furnace has been turned off, the temperature of furnace will keep going up because of the heating inertia inside furnace. So it is better to set about 80% of temperature you want to set normally before powering on the controller every time. After controller carry out “on-off control “for several times, then set temperature you want to set normally , so as to avoid over surging.
5.If the controller displays abnormally, check the sensor to see if its connection is open circuit or short circuit, also check if the working voltage of controller is normal.
Bottom Side Gusset Cat Food Packaging Bag Plastic Pouches
Injection Grade Hydroxypropyl-Beta-Cyclodextrin
High Precision Wood Laser Cutting Machine
Food Grade Hydroxypropyl Beta Cyclodextrin
Moisturizing Skin Foundation Cream
DIY Solar Charge Controller